The FMM‑7045 Multiplex Manual Stations are UL Listed fire alarm initiating devices that can be connected along with other multiplex devices on the D7039 Multiplex Expansion Module. The FPD‑7024 or D7024 Addressable Fire Alarm Control Panel (FACP) supervises the entire multiplex loop, including the FMM‑7045 or FMM‑7045‑D manual stations, for troubles, alarms, and ground fault conditions. Because each manual station occupies only one address on the multiplex bus, it can be addressed for any point within the 9 to 255 range allowed by the multiplex expansion module.
|Mux Bus Average Current Draw (alarm and standby )||0.55 mA|
|Voltage (operating)||12 VDC nominal (provided by the MUX bus)|
|Radio Frequency Interference (RFI) Immunity||No alarm on critical frequencies in the range from 26 MHz to 950 MHz at field strengths less than 30 V/m.|
|Temperature (operating)||+32°F to +120°F (0°C to +49°C)|
|Dimensions (L x W x H)||4.75 in. x 3.75 in. x 3.25 in. (12 cm x 9.5 cm x 8.2 cm)|
|Material||Die cast zinc alloy and steel|
|WeightGross Net||0.606 kg (1.34 lb.)0.420 kg (14.82 oz.)|